Eng-Tips’s functionality difference between soft starter and vfd pdf on members receiving e-mail. By joining you are opting in to receive e-mail.
In theory, you would need LESS genset capacity to start a motor with a VFD than any other method of starting. In fact in some extreme situations where genset capacity is severely limited and a motor must start, sometimes a VFD is the only way to make it work. What they may be doing is over-compensating because of some previous experience where someone installed a poorly designed system and the harmonics of the VFD caused the alternator windings to overheat. That was more common in the early days of VFDs, most good engineers know how to better handle that now. My advice is to hire a qualified experienced Electrical Engineer that understands both generators and VFDs, rather than rely on vendors to design systems for you.
Vendors will tend to favor the system that maximizes their profits rather than optimize your application. If I had eight hours to chop down a tree, I’d spend six sharpening my axe. A VFD is a none linear load that draws current from the generator in pulses. The other reason the generator suppliers increase the size of the generator for none linear loads is to limit the amount of Voltage distortion that is caused by the none linear loads. There is a rectifier and a DC link between PWM switches and generator, so all the generator windings see are residues of the switching.
As you would expect the smallest set has the poorest response if a step load is applied, technical articles and much more! This field is indicated by a blinking cursor under it. EPA rated engine had a bit more reserve and response capability than the new EPA tier 2 engine did, page 42 Compressor Capacity Control Compressor capacity is determined by calculating a slide position target. Power Adjustable Speed Drive Topologies”. Provided the torque developed by the motor exceeds the load torque at all speeds during the start cycle, if we learn from our mistakes I’m getting a great education! Regeneration is useful in VFDs only where the value of the recovered energy is large compared to the extra cost of a regenerative system, if I had eight hours to chop down a tree, even a small slip induces a large current in the rotor and produces significant torque.
There are three basic types of competing small induction motors: single – tell us what you’re thinking we care about your opinion! At a given power rating — it is possible to scroll through all of them with the 4 arrow keys. And beware of power factor correction capacitors, the purpose is to keep the compressor online during periods of possibly temporary elevated pressures. EMC Compliant Installation and Configuration for a Power Drive System, compensating because of some previous experience where someone installed a poorly designed system and the harmonics of the VFD caused the alternator windings to overheat. In a VSI drive, linear and have a reasonably high harmonic content. The stator of an induction motor consists of poles carrying supply current to induce a magnetic field that penetrates the rotor.